Clock Thermostat OCD2
4-Event OJ Microline®
- Clock Thermostat OCD2
OCD2 has built-in clock function and is provided 4-event program for automatic temperature control. The thermostat has adaptive function meaning the thermostat calculates when the heating has to be switched on to make sure that the comfort temperature is obtained at the required time. All settings and the clock are maintained if the thermostat is switched off by the built-in interrupter.
- Min. temperature limitation: For better heating comfort
- Max. temperature limitation: Protection of i.e. wooden floors
- 4-event Clock thermostat with 2 sensors
- Built in room sensor and floor sensor
How to tell whether it is an OCC2 or OCD2 thermostat?
- Press both UP and DOWN buttons together for 3 seconds. INFO is displayed.
- Press UP button until you reach the "APP" sub menu. Select the sub menu with the OK button.
- Try changing application type. If "roLi" is available the thermostat is a OCD2
Why does the thermostat keep clicking on and off rather than heating up?
We have a OCC2 for under floor bathroom heating. The thermostat / clock keeps clicking on and off every few seconds, when it is supposed to be heating up. The display goes blank and then reappears with an audible click for a few seconds. What is happening?
The internal power supply of the thermostat has over the years deteriorated. Please contact your local dealer for replacement.
What is the backup time on the OCC2?
The backup time on the OCC2/OCD2 is 48 hours.
What does error code "E2" mean?
Error code "E2" means defective, damaged or not connected floor sensor. Check connections or replace sensor if necessary.
What is the recommended night setback?
The recommended night setback is max 5°C/41°F
Does the adaptive function reset when making a factory reset?
Yes the adaptive function is reset during a factory reset.
Where to connect the ground wire of floor mats?
The ground wire in the floor mat must be connected directly to the ground wire of the supply.
Installation – Length of sensor cable
What is the maximum length of the sensor cable?
In general, it is recommended that the maximum sensor cable length should be 164 feet/50 meters, the length might be shorter. Read the instructions for the precise maximum length.
How can I cure the E2 error message?
"E2" means defective, damaged or disconnected floor sensor. Sensor resistance should be 10 or 12 kOhm at 25°C (77°F). The onstruction or quick guide holds informatiom for the specific thermostats.
Know How Creates ist unser Versprechen an Sie: Wir kanalisieren unsere Einsicht und Kompetenz, um damit die richtige Lösung zu finden
Hier finden Sie das Neueste für den Bereich elektrische Fußbodenheizungen von OJ Electronics
Intelligente Steuerungen ergeben einen Maximum an Komfort bei geringem Energieverbrauch.
Dialog und eine enge Zusammenarbeit ist der optimale Weg zu einer perfekten Lösung.